WT105 Conventional Heat Detector, Operates by Advanced MCU Expert Algorithm Software.
Key Specifications/Special Features
They work perfectly with all conventional intelligent fire control panels
Dual LEDs for 360-degree visibility
Advanced MCU Expert Algorithm Software.
Easy installation and maintenance
Durable sensor head, no need for replacement
SMD circuit board design-satisfactory quality and reliability guaranteed
This detector must be installed in compliance with the control panel installation manual and meet the requirements of the authority having jurisdiction. In addition, the National Fire Protection Association has published codes, standards, and recommended practices for the installation and use of detectors, NFPA 72.
Therefore, the installer must be familiar with these requirements, with local codes, and any special requirements of the authority having jurisdiction..
NOTICE: This manual should be left with the owner/user of this equipment.
IMPORTANT: The detector must be tested and maintained regularly following NFPA 72 requirements. The detector should be cleaned at least once a year.
The device is intelligent sensors that utilize a state-of-the-art thermistor sensing circuit for fast response. These sensors are designed to provide open area protection with 50 foot spacing capability. The device is a rate-of-rise temperature sensor with 135°F fixed temperature alarm.
The device is a rate-of-rise with fixed temperature alarm thermal detector utilizing a state-of-the-art dual thermistor sensing circuit. These detectors are designed to provide open area protection with 50-foot spacing capability, and are to be used with compatible control panels only.
Two LEDs on each detector light to provide 360° visibility of the detector indication.
NOTE: All wiring must conform to applicable local codes, ordinances, and regulations.
NOTE: Verify that all detector bases are installed, that the initiating-device circuits have been tested, and that the wiring is correct.
Remove power from initiating-device circuits before installing detectors.
1. Wire the sensor base per the wiring diagram, Figure 1.
2. Install the sensor into the sensor base. Push the sensor into the base while turning it clockwise to secure it in place.
3. After all sensors have been installed, apply power to the control unit.
4. Test the sensor(s) as described in the TESTING section of this manual.
5. Notify the proper authorities that the system is in operation.